ZECO is currently the only manufacturer in China with accurate KV data and support debugging services for balancing valve. We have our own dynamic water testing system, and all the differential pressure control valves and balancing valves used in the heating system and heating system are tested with accurate data, so as to lay a foundation for good balance effect in the later debugging service. Below are featured balancing valve for sale.
Types of Balancing Valve
How to Choose a Balancing Valve
Double regulating valves (DRV)
For flow regulation only.
Typically this valve is a Y pattern globe valve arranged in this way to present the smallest pressure loss to the system when fully open. Adjustment of this valve will add resistance to the system and hence reduce the flow. The description DOUBLE regulating means that it has a feature whereby you can set the position that the valve is to operate in such a way that you can still close the valve for maintenance purposes. When using computerized electronic manometers with a valve database you will not find any data relating to these valves because they do not have a measuring facility.
Flow measurement devices and valves (FMD/FMV)
For flow measurement with or without isolation facility.
These devices are usually fixed orifice devices. A fixed orifice is the simplest device that we can use for measurement. The fixed orifice can be used on its own or with an isolating valve fitted downstream to provide isolation. Installed on their own these devices can give the most accurate results. When using electronic manometry to display the flow through this product the Maker, model, and size of the unit must be entered into the meter.
Double regulating valves combined with flow measurement devices (FODRV)
For regulation and flow measurement combined in one valve unit based on the Fixed Orifice principle.
This combined assembly traditionally was assembled from a double regulating valve and fixed orifice device. More commonly nowadays the orifice is fitted directly into the body of the valve. When made up of a regulating valve and separate orifice the unit is often referred to as a ‘Commissioning set’ When using electronic manometry to display the flow through this product the Maker, model, and size of the unit must be entered into the meter.
Double regulating valves with integral flow measurement facility. (VODRV)
For regulation and flow measurement combined in one valve unit based on the variable orifice principle.
VODRV allows the measurement of the flow across the entire valve. There is no fixed orifice fitted to this valve – the signal measured on an electronic manometer relates to the loss across the whole valve When using electronic manometry to display the flow through this product the Maker, model, and size of the unit must be entered into the meter. Because the signal is measured on this valve relates to the loss across the entire valve the size of the signal depends on the position of the handwheel. This process will be dealt with in some detail later and really only affects those working on systems overseas.
How Does a Balancing Valve Work in HVAC Systems?
Balancing Valve in Fan-coil water system
The fan-coil system realizes the constant indoor temperature by controlling the switch of the two-position electric two-position valve. There are two commonly used methods to solve hydraulic imbalance. One is to install a balance valve on each layer of the return main pipe, and the other is to replace the two-position electric two-position valve at the end with a dynamic balance two-position electric two-position valve.
The balance valve should be selected according to the calculated capital pressure head and the flow rate; the balance valve system is a proportional system, and there is no problem of winter and summer conversion. The adjustment of the balance valve should ensure that the actual flow of each layer of main pipe under the design pressure difference is not greater than the design flow, so as to avoid excessive flow near the pump end loop and insufficient flow at the far end loop. The setting of the balance valve eliminates the residual pressure head of the system and avoids the waste of energy caused by the occurrence of overcurrent. Because it is a manual one-time debugging, when the pressure difference in the system changes, the resistance coefficient cannot be changed with the system changes, so it can only play a role of hydraulic balance within a certain range.
Balancing Valve in Water system of air-conditioning tank
The air-conditioning box realizes the constant indoor temperature by controlling the opening degree of the electric regulating valve. There are two commonly used methods to solve hydraulic imbalance. One is to install a balance valve in the return water main pipe, and the other is to replace the electric regulating valve at the end with a dynamic balancing valve electric regulating valve.
The setting of the balance valve is the same as the fan coil system. The fluctuation of the pressure in the pipeline of the electric control valve will affect the adjustment of the water volume, making it difficult for the air-conditioning box to meet the required water volume, so this method is not recommended.
The dynamic balance valve electric control valve has the characteristics of a self-operated flow control valve. Within the working pressure difference range, the water flowing through the fan coil can be maintained at a continuously adjusted set water volume without being affected by changes in pipeline pressure, avoiding the use of electric The disadvantages of the regulating valve are the above-mentioned disadvantages, so that the flow can be adjusted on demand, and the hydraulic balance is truly realized. The working pressure difference range is generally 30kPa～300kPa. In the range of the chilled water pump head below 35m, no other auxiliary regulating valve is needed, which simplifies the hydraulic balance system and shortens the time required for system design and commissioning.
Zeco is a manufacturer of accurate balancing valve KV value data and supporting debugging services in China and around the world. Why are we so confident? Firstly, as we have our own dynamic water testing system, we can conduct pressure difference test and flow test on various pressure differential valves and balancing valves in the heating system, which provides the most basic conditions for future debugging services. Second, in China, our energy-saving retrofit program for balance valves has been carried out for five years by thermal companies across the country, such as Beijing thermal group and Shandong thermal group for three years, all of which have obtained excellent energy-saving retrofit results. There are balance valves of various structures and shapes available on the global market.Although these manufacturers can improve the appearance of their products and boast about the performance of their products, when a single customer asks them to provide debugging services, they basically refuse or charge a high commission to make the customer back down. Why is that? Because they do not have specific KV value data, and they do not have their own energy saving balance system software for the entire system energy saving transformation.Balancing valve for customer, not buy a product so simple, for heating or HVAC system, it is a whole, not fitted with a balance valve can for system heat balance, it needs to carry on the preliminary analysis of the whole system, and according to the requirements of customers to configure the location of the balancing valve and differential pressure valve, and then simulate the thermal balance of the final result, after the confirmation and implementation of balancing valve installation, we’ll send the debugging of professionals with a debugging instrument developed by oneself to the scene debugging service, after the start of the heating, provide the energy saving report to customers.
Balancing Valve in Computer room system
The initial balance between parallel chilled water and cooling water circulating pumps is easier to achieve through the selection of pipeline and pipe diameter, but when multiple constant flow pumps are connected in parallel, after the number of pumps is reduced, if the pipeline characteristics do not change in the direction of increasing resistance, or The change is small (for example, the water pump is directly connected to the heat exchanger or shared header connection with the cooling tower. When the number of water pumps is reduced, the corresponding branch or equipment valve that is out of service is not closed), the flow of the running water pump will increase by a large amount , The motor of the water pump may be overloaded, so a self-operated flow regulating valve should be installed. If the number of units in parallel is small, a regulating valve or a three-function valve (regulation, check, shut-off) is generally added at the outlet of the water pump to adjust the resistance of the pipeline.
Water Control Solutions
ZECO has professional solutions to optimize water usage, reuduce costs and maximize energy efficiently.
ZECO Waterworks valves used in water supply are suitable for prolonged underground and outdoor use in demanding conditions and are maintenance-free.
ZECO HVAC valves control the flow balance and stabilise the differential pressure to achieve energy savings in HVAC systems.
Building & Construction
ZECO Building & Construction valves are widely used in commercial buildings and are used by the majority of well-known commercial companies and commercial buildings in China.
ZECO Fire Protection valves are able to cope with the emergency water piping needs of firefighting, guaranteeing the timely supply of water for firefighting and preventing the safety and stability of firefighting lines.
Oil & Gas
ZECO Oil & Gas Valve are used by oil companies in various countries and plays an important role in the safety and proper operation of oil pipelines.